Mark T. Kuntz and Justin Dawe
is sometimes harder to tell which is stronger: the public's love
affair with clean energy, or the headaches that utility planners experience
when they contemplate integrating these relatively new energy sources
into their already-stressed grids.
On the one hand, customers and the popular press have made it exceedingly
clear that they expect wind, solar, and other renewable energy sources
to play an increasingly important role in generating the electricity that
powers modern society. This desire is often driven by concerns about air
quality, public health, and energy security, among other factors.
|This 30 MW wind farm in Japan
is augmented by a battery system that can supply 4 MW of power for
up to 90 minutes.
On the other hand, utility planners who are working to match instantaneous
supply and load on their transmission and distribution infrastructure
often wonder how they will handle 5 percent penetration by intermittent
resources, much less the 20 percent or more that they are regularly told
is just around the corner. Go to any power engineering conference these
days, and you'll lose track of the number of times you hear seasoned
planners asking each other, "But what about when there's
no wind when you need it, or too much when you don't?"
As in so many cases where customers want something that providers are
not used to delivering, the answer lies primarily in the development and
application of new technologies. In this case, the technology family that
promises to bridge the gap is grid-scale energy storage. Modern energy
storage systems, capable of efficiently holding tens or even hundreds
of megawatt-hours of energy, could well make intermittent renewable energy
sources an attractive, reliable, and mainstream power option, even from
the demanding perspective of a utility planner. One technology in particular,
known as the flow battery, appears to have the combination of characteristics
necessary to connect today's customer desires with tomorrow's
integrated and clean energy system.
Before looking at how energy storage works, and what benefits it can provide,
it is worth understanding the challenges that wind and other renewable
energy sources create for utility planners. First, many renewables are
what are known as "intermittent" energy sources, meaning
that they aren't available all of the time or they cannot be called
upon at the utility's discretion.
For a utility planner, any intermittent source is therefore not "dispatchable."
A dispatchable energy source can be scheduled for use at the planner's
convenience. Traditional energy sources, such as coal, natural gas, and
nuclear-power thermal plants, are essentially completely dispatchablewith
exceptions for system malfunctions or breakdowns. Among renewable energy
sources, hydroelectric and geothermal facilities are also dispatchable,
within the natural limits of the resource availability.
The reason that dispatchability matters is that the electric grid requires
a constant and instantaneous match between the electric energy being generated
and that being consumed. Outside of the electric sector, there is always
a lag between supply and demand (think about grain in silos, the pipeline
of goods in a warehouse, or any typical supply chain). In the electric
sector, however, this buffer has traditionally been rarely available.
To make the balancing act work, utility planners lean on a mixture of
energy resources. Baseload facilities are operated at or near their maximum
capacity as much as possible, to serve the base of energy demand that
is always present. Coal-fired and nuclear power plants are the classic
baseload resources. Peaking plants are facilities that are then operated
to follow the ups and downs of the electric load. In recent decades, facilities
burning natural gas have been the fast-reacting power plant of choice
for this peaking role.
Customers on interruptible contracts, who agree to have their power turned
off at periods of peak demand in exchange for lower rates, provide a demand-side
option for balancing the equation.
fast rises and crashes
When you throw intermittent resources into the mix, matching energy supply
and load gets more complicated. Now, instead of just the fairly predictable
cycles of daily and seasonal load variations, there may be tens or hundreds
of megawatts of power that can come and go in an unpredictable fashion.
While there have been great strides made in forecasting methods, particularly
for wind, the resource itself is still fundamentally outside the control
of the utility planner. For the utility planner, these unpredictable changes
in power output come in two flavors: fast rises and crashes.
Fast rises in wind or solar power can be accommodated through power sheddingbasically,
the utility throwing away energy while it gets the system into balance.
More challenging, though, is when an intermittent energy source crasheswhen
the wind suddenly dies or a cloud suddenly blocks the sun. In this case,
the utility must have an energy source ready to pick up the slack; the
alternative is customers losing power. Unfortunately, while traditional
gas peaking plants can react quickly, even they generally need 15 minutes
or more to ramp up their power output.
In recent years, a number of energy storage technologies have been proposed
as a means of either making intermittent energy sources more dispatchable,
or at least helping utility planners bridge the gap between the fall-off
rate of renewables and the ramp-up rate of traditional peaking plants.
Hydroelectric dams were the first, and in some ways are still the best,
option under consideration. These facilities can react even more quickly
than gas plants to changing load, making them excellent bridging resources.
|A flow battery (shown here in
a three-dimensional rendering) stores energy electrochemically in
the form of vanadium ions suspended in a solution.
In places where a significant amount of wind power is being generated,
that wind power can be used to pump water below the dam back up into a
reservoir, essentially storing the power for later use. Better yet, this
type of pumped hydro resource is relatively cheap, and the fact that it
is renewable makes it an excellent complement to wind power, which is
often developed in the first place to cut down on environmental impacts.
In places such as the Pacific Northwest, integration of wind and hydro
has become relatively common. Unfortunately, there is a limited amount
of hydropower, and it is not necessarily available in the same places
where excellent wind resources can be found.
Another storage technology that has received attention is compressed air
energy storage. In this case, wind power is used to compress air in an
underground chamber; the compressed air is later released to help drive
a turbine that generates electricity. Like pumped hydro, there are no
technical limits to the implementation of large projects. Unfortunately,
the geologic formations necessary for compressed air storage are relatively
rare, meaning that it likely will never be a major contributor to the
national energy system.
Traditional electrochemical batteries, including lead-acid batteries,
are another option. For remote communities that have long needed energy
storage, lead-acid batteries are viable but problematic tools. Due to
cost and performance limitations, particularly their relatively short
lifespans, large-scale lead-acid battery installations are not an adequate
complement to intermittent renewable energy sources.
And, of course, no discussion about achieving a clean energy future would
be complete without mention of fuel cells and the hydrogen economy. Fuel
cells convert hydrogen (or other fuels) into electricity without combustion,
and their successful mass commercialization could radically alter the
way that power is generated in both stationary and mobile applications.
Some fuel cell proponents envision a day when wind farms and other clean
energy sources power massive water electrolyzers, generating the hydrogen
that fuel cells would use, in turn, to power the economy. While this type
of arrangement would indeed represent a comprehensive energy system, it
faces significant technological and economic hurdles.
juice in, juice out
All of this brings us to a novel type of battery known as a flow battery.
Flow batteries essentially comprise two key elements: cell stacks, where
power is converted from electrical form to chemical form, and tanks of
electrolytes where energy is stored.
The most popular flow battery on the market uses a vanadium redox technology,
using charged vanadium in a dilute sulfuric acid solution to store energy.
The appeal of flow batteries is that for grid applications they combine
the strengths of both conventional batteries and fuel cells.
Like a fuel cell, a flow battery has a long life and is both energy-efficient
and environmentally friendly. Also, like a fuel cell, the energy rating
of the system is a separate design variable from the power rating. Increasing
the volume of the electrolyte tanks increases the amount of energy that
the system can store and release; increasing the number of cell stacks
increases the power that the system can generate.
Like traditional batteries, but unlike fuel cells, flow batteries are
an "electricity in, electricity out" system. There is no
external fuel source, such as hydrogen, that is added regularly to recharge
the system. Instead, electric energy is supplied to the system at one
time, and the system stores that electric energy in electrochemical form
until it is needed later. For grid applications, this simpler arrangement
avoids the need to create new fuel or distribution systems.
In addition, unlike fuel cells, flow batteries are not based on rare or
valuable materials. Fuel cells typically use platinum or other expensive
catalysts to speed the oxidation of their energy carrier. Instead, the
material at the heart of a flow battery cell is vanadium, a plentiful,
While a flow battery using an electrolyte solution doesn't have
the same energy density as a fuel cell using hydrogen as an energy carrier,
for most grid applications high energy density is not a key design factor.
Because of this lower energy density, you won't see a flow battery
powering a car on the street, but the price and performance do create
the potential for significant grid applications.
|Pipes and pumps carry the vanadium
solution to stacks of proton exchange membranes, which transfer electrical
charge and create a current.
One early application of flow battery technology in the United States
was a project developed in a partnership between the large western utility,
PacifiCorp, and VRB Power Systems, a Vancouver, British Columbia, developer
of vanadium-based flow battery energy storage systems. The project, located
in Castle Valley, Utah, involves a 250 kW installation with an eight-hour
storage capacity. In energy terms, this is a 2 MWh system.
Installed in 2003, the Castle Valley system is charged overnight by baseload
resources, and supplements the supply of power to a small community during
the hottest part of the day, when the distribution feeder is overloading.
This arrangement helped PacifiCorp avoid having to install a new transmission
line to Castle Valley, and increased the utilization of existing infrastructure.
Nearly two-dozen other flow battery systems are in place around the world,
with tens of thousands of reliable charge-discharge cycles on record.
Flow batteries also appear to match up quite well with the needs of utility-scale
wind farms. In Japan, where utilities are required to generate a portion
of their energy from renewable sources such as wind, the utility J-Power
added a 4 MW, 90-minute (6 MWh) vanadium-based flow battery to an existing
30 MW wind farm.
The wind farm charges the storage system, and the storage system serves
to level the output of the wind farm to the broader distribution grid.
When the wind rises or falls over the course of a few seconds, the storage
system smooths the frequency variations that would normally arise. This
protects energy consumers from deviations in their expected power quality.
When the wind suddenly cuts out more than that, though, the flow batteries
really earn their keep. In those cases, the flow batteries can provide
burst power up to 6 MW, creating the power bridge that gives utility operators
the chance to bring peaking plants or other generation resources online.
The additional layer of equipment adds perhaps 15 percent to the cost
of a stand-alone wind farm, but more than makes up for the additional
cost by increasing the value of the electricity that's generated.
As with any relatively new technology, there are a few chasms that must
be crossed before widespread development of wind-integrated flow battery
systems occurs. VRB Power Systems and others are working to build the
capacity to supply products in volume to the market, as well as to build
market awareness of the technology and to continue to drive down the cost
of manufacturing the energy storage systems. Just as importantly, utilities
are beginning to understand how energy storage can increase the value
of their existing system resources, and how it can help them reshape their
resource base over time, if necessary.
The notion of complementary ramp ratesof flow batteries and peaking
plants matching the falloff from wind farmsis beginning to be
discussed and fine-tuned by utility planners. Utilities such as J-Power
and PacifiCorp, by installing flow batteries on their grids, are providing
invaluable real-world proving grounds and racking up years of performance
records that will ultimately make or break the market.
In short, energy storage technologies are rapidly being commercialized
to enable the widespread integration of intermittent renewable energy
sources into the grid. Hydropower, compressed air, flow batteries, and
other technologies continue to be fine-tuned as tools for the utility
planner's tool belt. The increasing understanding of how storage
can build a bridge from wind power to dispatchable resources creates options
that were not available even a few years ago. And, as the months go by,
these technologies make it more feasible for an increasingly reliable,
clean, and secure electric energy system to emerge.
How Flow Batteries
Working like a cross
between a standard lead-acid battery and a fuel cell, flow batteries
have been around since the 1880s, when one was used to power an
airship. After decades of neglect, the concept of the flow battery
was picked up by research groups in Australia and Japan in the mid-1980s.
Derived from a patented vanadium-based
redox regenerative fuel cell, VRB's flow batteries convert chemical
energy into electrical energy. Energy is stored chemically in different
ionic forms of vanadium within a dilute sulfuric acid electrolyte.
The electrolyte is pumped from separate plastic storage tanks into
flow cells across a proton exchange membrane where one form of electrolyte
is electrochemically oxidized and the other is electrochemically
reduced. This creates a current that is collected by electrodes
and made available to an external ciurcuit. The reaction is reversible,
allowing the battery to be charged, discharged, and recharged.
Mark T. Kuntz is vice president for marketing and business development
at VRB Power Systems in Vancouver, British Columbia. Justin Dawe also
works at VRB, as a marketing analyst.
| features | breaking
news | marketplace
| departments | about
ME back issues | ASME
| site search
© 2005 by The American Society
of Mechanical Engineers